Microsoft word - k123-2e_en.doc
K-1 2E, K-2 2E, K-3 2E
The magnetic contacts consist of two elements: magnetic sensor (reed switch) and
magnet. The reed switch, which is situated near the magnet, makes the electric circuit.
Each of the magnetic contact elements is
placed in an identical watertight housing, the
part with reed switch having electric lead-
outs (Fig. 1,2,3). Inside the housing together with the reed switch are installed two 1.1kΩ
Fig. 1 K-1 2E reed switch in plastic housing
resistors connected with the reed switch in 2EOL configuration (see Fig. 5). They enable
the control panel to detect a tamper of the magnetic contact by monitoring the resistance changes on the zone. Each detector of this type must be connected to a
Individual magnetic contacts differ in the
Fig. 2 K-2 2E reed switch in plastic housing
housing style and the way of mounting. The K-1 2E is designed for surface mounting and the K-2 E & K-3 2E for flush mounting.
wherever required for controlling the status of doors, windows and/or other movable elements, e.g. for protection or monitoring of
access to particular sites, spaces, facilities;
Fig. 3 K-3 2E reed switch in metal housing
INSTALLATION – Fig. 4
The magnetic contact element containing the magnet should be mounted on the movable part, while the
reed switch – on the stationary part of protected doors, windows, etc. Elements of the K-1 2E magnetic
contact should be attached to the surface by means of screws, suitable glue, or a two-side self-adhesive
tape. The K-2 E & K-3 2E magnetic contacts are designed for face mounting in such materials as wood
or plastic (Fig. 4). The walls, the magnetic contact is to be fitted in, should be at least 10mm thick, so as
to ensure adequate stability for the elements mounted. To make holes for the K-2 2E
drill, and for the K-3 2E
magnetic contact – ø9mm
drill. The K-2 2E is to be pressed in, while
the K-3 2E, which has a thread, needs to be screwed in. The mounted magnetic contact elements can
be reinforced with a suitable glue.
In order to ensure correct functioning of the magnetic contact, the distance between magnet and reed switch should not exceed 12–15mm for K-1 2E & K-2 2E, and 15–18mm for K-3 2E. Misalignment of the axes of magnet and reed switch in cylindrical magnetic contacts should not be greater than 10mm for K-2 2E and 12mm for K-3 2E.
• You are in no case allowed to shorten (cut short) the element containing the magnet.
• Special care must be taken when installing reed contact part of the detector. It should not be
hammered into the slot, because the fragile component inside the detector might be damaged then.
• When screwing the K-3 2E reed relay in, the wire will get twisted; to prevent it from damage, make
sure that it has a sufficient spare length, or twist it in the opposite direction before installation so that it can straighten out when mounted.
Fig. 4 Example of face mounting of K-3 2E magnetic contact
HOOKUP – Fig. 5
Fig. 5 Connection of the magnetic contact with 2EOL resistor to the control panel.
Magnetic contact type .2EOL/NC Resistance.2x1.1kΩ Maximum switchable voltage of reed switch .200V Maximum switchable current .500mA Maximum continuous (non-switchable) current .1.5 A Rated power . 10 VA Minimum number of switchings under load
PREFERRED THERAPIES: (additional pediatric-specific formulations appear in blue) Most Common Approx Cost Non-Formulary Approx Cost Drug Class Formulary Agent Per Month‡ Per Month‡ Penicillins Augmentin XR 2gm BID BPA, F3, $165/10days Allergy Drugs Analgesics Antidepressants Hyperlipidemics Hypertensives Infectives Allergy Drugs Analgesics A
NAHAR CAPITAL AND FINANCIAL SERVICES LIMITED The Register of Members and Share TransferRegister of the Company shall remain closed fromNotice is hereby given that the 4th Annual General23rd September, 2009 to 30th September, 2009Meeting of the Members of Nahar Capital and FinancialServices Limited, will be held on Wednesday the 30thday of September, 2009 at 11:00 A.M. at the M/s. NaharThe